1Capacity available for user.
2A Lithium battery's lifetime is:
10 years when the battery's ambient temperature is 40 oC or less.
4.1 years when the battery's ambient temperature is 50 oC or less.
1.5 years when the battery's ambient temperature is 60 oC or less.
When used for back up: Approximately 100 days, with a fully charged battery.
Approximately 6 days, with a half-charged battery.
3Depending on the operating temperature and age of unit, the clock can deviate from -380 to +90 sec./month. For systems where this level of deviation is a problem, the user should monitor and make adjustments when required.
4The front face of the GP unit, installed in a solid panel, has been tested using, conditions equivalent to the standards shown in the specification. Even though the, GP unit's level of resistance is equivalent to these standards, oils that should have, no effect on the GP can possibly harm the unit. This can occur in areas where either, vaporized oils are present, or where low viscosity cutting oils are allowed to adhere, to the unit for long periods of time. If the GP's front face protection sheet becomes, peeled off, these conditions can lead to the ingress of oil into the GP and separate, protection measures are suggested., Also, if non-approved oils are present, it may cause deformation or corrosion of the, front panel’s plastic cover. Therefore, prior to installing the GP be sure to confirm the, type of conditions that will be present in the GP's operating environment., If the installation gasket is used for a long period of time, or if the unit and its gasket, are removed from the panel, the original level of the protection cannot be guaranteed., To maintain the original protection level, be sure to replace the installation gasket, regularly.
5Regarding dimensional tolerance, everything +1/-0 mm [+0.04/-0 in.] and R in angle are below R3 [R0.12 in.].